Originally Posted by 3950 1MODAY
There is a recall on a solinode that gets to hot on the frig and it is a fire hazard. It does not get cold enough for me Hot summer days at the beach it struggles to keep up. So I want to put in a residential frig.
I understand the frustration, I was having similar issues other than the recall. I did a lot of trouble shooting and research! Come to find out I was chasing an issue that was not the refrigerator. The issue ultimately was the voltage. Over night it was fine and during the day it would get in the 50's. Voltage was dropping during the day and the coils were not keeping up.
Have you tried running on Propane during the day or the generator? Do you know how to access diagnoses mode? Diagnoses mode on number 3 will tell you the temperature of fins on the inside of the fridge. Try not to open while testing.
2014 Voltage 3950 Epic III
2016 Ram 3500 Diesel 4wd, Long Horn Dually long bed